A Lesson in Repairing Cracked Kaplan Bladesby Robert van der Borg, Bonneville Lock & Dam, Cascade, Locks, OR, USA,
Document Type: Proceeding Paper
Part of: Water Power '87
Each of the three units that failed at Bonneville Lock and Dam started with a fatigue break and ended in a brittle fracture. Consequently, a comprehensive in-house weld procedure was developed to repair the cracks in the turbine runner blades. Details of this procedure are given.
Services: Buy this book/Buy this article
Return to search