Voltage Regulator Influence on Generator System Stabilityby Richard C. Schaefer, Basler Electric, Highland, United States,
Abstract: During initial startup of a generator system, it is not uncommon to witness generator voltage instability. Most of the time, the solution is reduced to returning the stability control on the automatic voltage regulator until the generator voltage has normalized. In this paper various factors that cause generator instability will be discussed. These include the field time constants of the generator as related to machine speed and size, and the characteristics of the voltage regulator whose stability network, for optimum performance, needs to be tuned to match the field time constants of the machine. Another important criteria is the definition of 'What is good voltage regulator stability?' Here guidelines will be offered providing basic steps in tuning the voltage regulator with an explanation of more elaborate methods utilizing more complex hardware. In addition, computer modeling will be used to assist in demonstrating the affect of more or less stability as it affects generator performance. Lastly an examination will be made of other types of instability as affected by the excitation system.
Subject Headings: Equipment and machinery | Computer models | Electric power | Electrical systems | Automation | Terminology and definition | Computer aided operations | Excitation (physics)
Services: Buy this book/Buy this article
Return to search