Tracer Study for C*t Compliance Evaluationby Christopher H. Yu, McDonnell Engineering Co, Kansas City, United States,
Bruce J. Hattig, McDonnell Engineering Co, Kansas City, United States,
Michael J. O'Connell, McDonnell Engineering Co, Kansas City, United States,
Document Type: Proceeding Paper
Abstract: A tracer study was performed with a fluorescent dye, Rhodamine WT, to determine the actual disinfectant contact time for the 36-mgd Courtney Bend Water Treatment Plant near Independence, Missouri, The results indicated that the plant will be in compliance with the C*t requirement of the Surface Water Treatment Rule (SWTR) and an addition of settling basin would not be required for the latest 6-mgd expansion of the plant.
Subject Headings: Water treatment plants | Water supply | Probe instruments | Water quality | Surface water | Settling basins | Dyes | North America | Missouri | United States
Services: Buy this book/Buy this article
Return to search