Lateral Loads on Power Boilersby Hugh W. Hempel, (F.ASCE), Staff Civ. Engr.; Stearns-Roger, Inc., Denver, Colo.,
Serial Information: Journal of the Energy Division, 1979, Vol. 105, Issue 2, Pg. 241-250
Document Type: Journal Paper
Abstract: The structural section of power-boiler specifications should include lateral-force design criteria to minimize the possibility for critical damage and resulting financial loss during a furnace explosion. Boilers designed for 20% g have survived violent explosions with moderate structural damage. In areas of low seismicity, reasonable protection can be attained by specifications requiring minimum lateral design forces of 10% g and redundant bracing systems with strong and ductile connections that will bend and not rupture under out-of-plane loading.
Subject Headings: Lateral loads | Lateral forces | Damage (structural) | Explosions | Seismic loads | Seismic design | Financial management | Seismic tests |
Services: Buy this book/Buy this article
Return to search